Product introduction of ultrasonic humidifier in curing room:
The ultrasonic humidifier in the curing room is a new product developed by our company. It adopts ultrasonic negative ion humidification. The ultrasonic humidifier in the curing room is widely used in the maintenance of test blocks in highways, bridges, railways, buildings, and water conservation standard curing rooms. It can also be used in textile, agriculture, medical treatment, food processing, etc. It is an ideal product for laboratories and production workshops with high humidity requirements.
Technical parameters of ultrasonic humidifier in the curing room:
★ Power supply voltage: 220AVC Atomized water volume: ≥3000ml / hr
★ Working voltage: 48VDC atomizing particle diameter: 1-10u
★ Working current: 42-5.0A Transducer life: 3000-5000hr
★ Power: 300W A best water temperature: 30 ± 5 ℃
★ Dimensions: 400X320X400mm Applicable volume: 20-100m3
Third, the operating steps of the ultrasonic humidifier in the conservation room:
★ Disconnect the power of the atomizer, remove the atomizer and wipe the atomizer clean;
★ Remove the packaging bag for the spare parts of the transducer sheet, take out the tool spoon and spare atomizing transducer sheet;
★ Unscrew the pressure ring of the atomizer with a tool spoon, take out the pressure ring and the transducer in the transducer cavity;
★ Clean the dirt and sundries in the transducer cavity and wipe the transducer cavity with a soft cloth;
★ Put the new transducer into the transducer cavity (note the orientation of the transducer during assembly), and tighten the pressure ring with a tool spoon.
Fourth, the installation steps of the ultrasonic humidifier in the conservation room:
★ Choose the right place to put the humidifier
★ Connect the water pipe to the water inlet of the humidifier filter
★ Fill the water tank (this product is automatic water level adjustment)
★ Connect the humidifier power cord and fan power cord to the corresponding power supply
① Host power supply is connected to 48VDC
② Fan power is connected to 24VDC
★ Connect the switching power supply to the corresponding control equipment
(200VAC) can be put into work, please refer to the wiring diagram (1)
V. Spare parts and use methods of ultrasonic humidifier transducer in curing room
Under normal use of the transducer surface, the service life of the transducer is about 3000-5000 hours. When the atomization amount is significantly attenuated, please clean the scale or impurities on the surface of the transducer sheet. If the atomization amount is still insufficient after cleaning, , You need to replace the transducer.
Six, the characteristics of ultrasonic humidifier in the conservation room
The integrated input ultrasonic humidification movement has the advantages of no mechanical drive, low noise, high efficiency, and large atomization. During work, the water enters the tank through the filter, and the atomizer generates high-frequency negative ions with a certain frequency, which is discharged by the fan. The filter can remove the sediment, rust, etc. in the water, with high efficiency, large flow and long life And easy to maintain, further extend the life of the atomizer. The box is made of engineering plastics, which is pressure-resistant, high-temperature-resistant and has good corrosion resistance. At the same time, it uses double outlets and the direction can be adjusted at will to make the humidity more uniform. The switching power supply provided by this machine uses 220V AC, outputs 48VDC for the atomizer, and 24VDC for the fan, ensuring the user's safety.
Note: This machine is equipped with a built-in electronic temperature control protection switch (disconnection temperature is 65 ± 5 ℃, reset temperature is 40 ± 5 ℃) and water shortage protection switch. Please use it with confidence.
Seven, maintenance and repair precautions of ultrasonic humidifier in the conservation room
★ When using this humidifier, please be sure to use the switching power supply provided by our company. After the wiring is completed, the switching power supply should be fixed to a dry, hard-to-touch location such as a wall, and do not touch any part of the power supply during work to prevent electric shock The place where the switching power supply is placed should be well ventilated, and the surface temperature will be as high as 40-50 ° C during work. Please rest assured.
★ When you need to use the humidifier in groups, please be sure to provide power separately according to the requirements. Do not use a single power supply to connect multiple humidifiers to work.
★ After the humidifier works for a period of time, because scale will be deposited on the surface of the atomizer transducer sheet, which directly affects the amount of fog, it is recommended to clean it every 2-3 weeks, and wipe the transducer sheet with a soft cotton cloth to remove dirt (Do not use corrosive detergents such as washing powder and detergent) to keep the humidifier A in good working condition.
Note: The cleaning cycle can be shortened or prolonged appropriately according to the water quality in different places.
★ After long time work (about 3000 hours), the atomization amount of the atomizer will gradually decrease. At this time, please refer to Figure (2) to replace the atomizer with a new one.
★ Clean the filter element regularly. If it is blocked by dirt for a long time, it needs to be replaced.
★ It is strictly forbidden to inject corrosive liquid into the water tank to ensure the normal operation and service life of the humidifier.